WP-8448 - Win-GRAF based WinPAC-8000, 4 I/O Slots
Win-GRAF based WinPAC-8000 PAC Programmable Controller with 4 I/O Slots, WinCE 5.0, IEC-61131-3, .NET
The Win-GRAF WinPAC-8000 Series (WP-8448) is the new generation IEC-61131-3 compliant WinCE 5.0 based Win-GRAF PAC (Programmable Automation Controller) from ICP DAS. Each WP-8xx8 is equipped with a PXA270 CPU (520 MHz) running a Windows CE 5.0 operating system, a variety of input/output ports (VGA, USB, Ethernet, RS-232/485), and a range of I/O slots that can be used to integrate high performance parallel I/O modules (high profile I-8K Series) or serial I/O modules (high profile I-87K series).
The benefits of running Windows CE 5.0 on a WinPAC device include hard real-time capability, achievable deterministic control and allowing PAC can have a PC-like window displays and operating environment. The WP-8xx8 series PACs are capable of running Win-GRAF (IEC 61131-3 Standard) software to develop logic control applications, and also supporting M.S. VS 2008 or VS 2010 software (VB .NET, C#) to develop HMI and data management applications that can exchange data with Win-GRAF applications. So the application's design is more convenient and more practical.
- PXA270, 520 MHz CPU
- Windows CE 5.0
- Embedded Win-GRAF SoftLogic (IEC 61131-3)
- Hard Real-Time Capability
- VGA Port Output
- Modbus RTU/TCP (Master, Slave)
- Support Soft-GRAF HMI
- Redundant Power Inputs
- Operating Temperature: -25 ~ +75 °C
- IEC-61131-3 compliant
Win-GRAF Workbench Features
Win-GRAF is a powerful, PLC-like, softlogic development software. It is installed on PC with windows 7 or 8. It supports the international PLC language standard - IEC 61131-3 - Ladder Diagram (LD), Function Block Diagram (FBD), Sequential Function Chart (SFC), Structured Text (ST), Instruction Set (IL), suitable to develop applications for the full range of Win-GRAF PACs from ICP DAS.
- IEC 61131-3 Standard Open PLC Syntax (LD, FBD, SFC, ST, IL)
- Using ST Syntax in the FBD or LD Program
- Data Binding (Exchange Data between PACs)
- On Line Debug/Control/Monitor, Off Line Simulation
- On Line Change
- Various Protocols:
- Modbus TCP/UDP, Modbus RTU/ASCII Master
- Modbus TCP, RTU Slave
- DCON, etc
- Plenty of Functions, Function Blocks, I/O Boards
- Redundancy (For XP-8xx8-CE6 and XP-9xx8-CE6 PAC only)
These applications apply to Win-GRAF PACs
On Line Change
Replace the current running project to a new modified one without stopping the project.
Modbus Master Ports
The WP-8xx8 connects to the slave devices
Soft-GRAF Colorful HMI
Our powerful software package interfaces with out modules and affects the I/O controls
Modbus RTU/TCP Slave Ports
The WP module interacts through it's slave ports
Exchange data between PACs.
DCON Remote I/O
Input / output remotely through DCON
2G/3G Wireless Application
- The Win-GRAF PAC equipped with RMV-531 (MultiPort Serial to 2G/3G Gateway) module (require a SIM card provided by a local telecom company) can be used to remote download and debug Win-GRAF program from a PC via 2G/3G wireless signal for maintenance requirements at hard-to-reach places.
- The Win-GRAF PAC equipped with RMV-531 (MultiPort Serial to 2G/3G Gateway) module (require a SIM card provided by a local telecom company) allow the InduSoft (PC/ HMI SCADA) to request the Win-GRAF PAC by means of the Modbus RTU Master via 2G/3G wireless signal. It applies to distributed systems with data logger requirements at hard-to-reach places.
Support VS 2008/VS 2010 Development
- The Win-GRAF PACs support to use VS 2008 or VS 2010 (VB.net, C#) to develop user own HMI and data management programs, and can exchange variables with the Win-GRAF control programs.
Reference & Support
|OS||Windows CE 5.0|
|.Net Compact Framework||3.5|
|Embedded Service||FTP Server, Web Server|
|Multilanguage Support||English, German, French, Spanish, Russian, Italian, Korean, Simplified Chinese, Traditional Chinese|
|Win-GRAF Software||Win-GRAF||IEC 61131-3 standard|
|Languages||LD, ST, FBD, SFC, IL & FC
Supports Soft-GRAF HMI : WP-8xx8, WP-5xx8, XP-8xx8-CE6, XP-9xx8-CE6 and VP-25W8/4138 PAC.
|Max. Code Size||2 MB|
|Scan Time||3 ~ 15 ms for normal program
15 ~ 50 ms for complex or large program
|Non-Win-GRAF||Options: VS.NET 2008/2010 (VB.NET, C#.NET, C)|
|CPU||PXA270, 520 MHz|
|Fast Retain Memory||512 KB (for retain variables)|
|Memory Expansion||microSD socket with one microSD card (support up to 32 GB)|
|RTC (Real Time Clock)||Provide second, minute, hour, date, day of week, month, year|
|64-bit Hardware Serial Number||Yes, for Software Copy Protection|
|Dual Watchdog Timers||Yes|
|Programmable LED Indicator||1|
|Rotary Switch||Yes (0 ~ 9)|
|DIP Switch||-||Yes (8 bits)||Yes (8 bits)|
|VGA & Communication Ports|
640 x 480, 800 x 600
|Ethernet||RJ-45 x 2, 10/100 Base-TX (Auto-negotiating, LED indicators)|
|USB 1.1 (Host)||1|
|COM0||Internal communication with the high profile I-87K series modules in slots|
|COM1||RS-232 (to update firmware) (RxD, TxD and GND); non-isolated|
|COM2||RS-485 (Data+, Data-) with internal self-tuner ASIC;
2500 VDC isolated for WP-8147; 3000 VDC isolated for other models.
|RS-232/RS-485 (RxD, TxD, CTS, RTS and GND for RS-232; Data+ and Data- for RS-485);
|RS-232 (RxD, TxD, CTS, RTS, DSR, DTR, CD, RI and GND); non-isolated|
|I/O Expansion Slots|
|Note: For High Profile I-8K and I-87K Modules Only|
|Dimensions (W x L x H)||95 mm x 132 mm x 111 mm
||231 mm x 132 mm x 111 mm||355 mm x 132 mm x 111 mm|
|Installation||DIN-Rail or Wall Mounting|
|Operating Temperature||-25 ~ +75 °C|
|Storage Temperature||-30 ~ +80 °C|
|Ambient Relative Humidity||10 ~ 90 % RH (non-condensing )|
|Input Range||+10 ~ +30 VDC|
|Redundant Power Inputs||Yes, with one power relay (1 A @ 24 VDC) for alarm|
|Capacity||8 W||30 W||30 W|
|Power Consumption||7.3 W||9.1 W||9.6 W|
|Protocols (Note that certain protocols require optional devices)|
|NET ID||1 ~ 255, for Modbus TCP/RTU Slave, user-assigned.|
|Modbus TCP/IP Master||A max. of 32 IP links to access/control the devices supporting Standard Modbus TCP Slave protocol.|
|Modbus RTU/ASCII Master||A max. of 36 ports: COM1 ~ 37 (*) to connect other Modbus Slave devices(Like M-7000).
Recommend connecting no more than 32 devices in each port for better scan rate.
|Modbus RTU Slave||A max. of 16 ports: COM1 ~ 37 (*) for connecting SCADA/HMI/OPC Server.|
|Modbus TCP Slave||Two Ethernet ports (LAN1 & LAN2) support up to 32 connections. If the PAC uses 1 connection to connect each PC/HMI, it can connect up to 32 PCs/HMIs; If the PAC uses 2 connections to connect each PC/HMI, it can connect up to 16 PCs/HMIs; If one of the Ethernet port malfunctions, the other one can still be used to connect the PC/HMI.|
|User-defined Protocol||Custom protocols can be applied at COM1~ 37 (*) by using Serial communication functions or function blocks.|
|DCON Remote I/O||A max. of 16 RS-485 ports: COM1 ~ 37 (*). Each port can connect max. 50 nos I-7000 series modules or
50 nos I-87xxxW I/O modules in expansion units (I-87K4, I-87K8, I-87K9, RU-87P8, RU-87P4).
Recommend connecting no more than 32 modules in each port for better scan rate.
|Local I/O Modules||Supports only high profile I/O modules. Slot 0~7 supports I-8xxxW parallel I/O modules and I-87xxxW serial I/O modules. (Refer Optional I/O List)|
|App Protection||Using the unique 64-bit (8 bytes) PAC serial number to generate a protection password by your own algorithm to protect your Win-GRAF application. Then, if someone intend to copy your application in the PAC to another new PAC with the same PAC model, this application will not work properly in that new PAC.|
|Data Binding||Used to exchange data between ICP DAS Win-GRAF PAC via Ethernet ports (LAN1 and LAN2). And can setup the Redundant Binding by Software, then if one Ethernet port fail, it can switch to use the other port.|
|On Line Change||For application field that not allowed to stop the Win-GRAF program and wish to run a new program modified a little from the original program.|
|Modbus RTU I/O||When software enables Modbus RTU Master function, the PAC can connect ICP DAS M-7000 and tM series and LC series I/O modules which support Modbus RTU protocol.|
|Modbus TCP I/O||When software enable Modbus TCP Master function, the PAC can connect ICP DAS I-8KE4/8-MTCP, PETL-7000, tPET/tET series I/O modules which support Modbus TCP protocol.|
|Retain Variables||Built-in the fast retain memory that can retain up to 12,000 Win-GRAF variables.|
|File Access and Data Log||The Win-GRAF supports file operation functions to read/write files in the PAC's micro_SD or flash memory to do data log or file access.|
|Soft-GRAF HMI||Support to run HMI program (developed by the Soft-GRAF Studio) together with the Win-GRAF logic-control program in the same PAC.|
|Optional I/O List (Go to I-8K, I-87k Selection Guide)|
|Digital Input (DI)||I-8040W, I-8046W, I-8051W, I-8052W, I-8053W, I-8053PW, I-87040W, I-87040PW, I-87046W,
I-87051W, I-87052W, I-87053W, I-87053PW, I-87053W-A2, I-87053W-A5, I-87053W-E5
|Digital Input/Output (DIO)||I-8042W, I-8050W, I-8054W, I-8055W, I-87042W, I-87054W, I-87055W|
|Digital Output (DO)||I-8037W, I-8041W, I-8041AW, I-8056W, I-8057W, I-87037W, I-87041W, I-87057W, I-87057PW|
|Relay Output||I-8060W, I-8063W, I-8064W, I-8068W, I-8069W, I-87061W, I-87061PW, I-87063W, I-87064W,
I-87065W, I-87066W, I-87068W, I-87068W-2A, I-87069W, I-87069PW
|AC Input||I-8058W, I-87053W-AC1, I-87058W, I-87059W|
|Analog Input (AI)||I-8017DW, I-8017HW, I-8017HCW, I-87017W, I-87017RW, I-87017RCW, I-87017DW, I-87017EW,
I-87018W, I-87018RW, I-87018PW, I-87018ZW, I-87019PW, I-87019RW, I-87019ZW
|Analog Output (AO)||I-8024W, I-87024CW, I-87024UW, I-87024DW, I-87024RW, I-87024W, I-87028CW, I-87028UW,
|Multifunction (DIO, AIO)||I-87026W|
|RTD||I-87013W, I-87015W, I-87015PW|
|T/C||I-87018W, I-87018RW, I-87018PW, I-87018ZW, I-87019PW, I-87019RW, I-87019ZW|
|Counter/Frequency Input||I-8084W, I-87082W, I-87084W|
|Communication Module||I-8112iW, I-8114W, I-8114iW, I-8142iW, I-8144iW|
|Temperature & Humidity Input||DL-100T485, DL-100T485-W, DL-100T485P, DL-100T485P-W (DCON Protocol)
DL-100TM485, DL-100TM485-W, DL-100TM485P, DL-100TM485P-W (Modbus RTU Protocol)
|* Note: COM6 ~ COM37 ports are located in the expansion boards if they are installed in slot 0 ~ 7 of WP-8xx8.
* WP-8148 has no COM3 and COM4.
* ICP DAS recommends using NS-205/NS-208 or RS-405/408 (Ring Switch) Industrial Ethernet Switches.