7.0 on a WinPAC device include hard real-time capability, achievable deterministic control and allowing PAC can have a PC-like window displays and operating environment. The WP-8428-CE7 is capable of running Win-GRAF (IEC 61131-3 Standard) software to develop logic control applications, and also supporting M.S. VS 2008 software (VB .NET, C#) to develop HMI and data management applications that can exchange data with Win-GRAF applications. This allows the application's design more convenient and more practical.
- Cortex-A8, 1GHz CPU
- 512 MB DDR3 and 256 MB Flash
- Windows CE 7.0 Professional
- Embedded Win-GRAF SoftLogic (IEC 61131-3)
- Hard Real-Time Capability
- VGA Port Output
- Modbus RTU/TCP (Master, Slave)
- Support eLogger HMI
- Redundant Power Inputs
- Operating Temperature: -25 ~ +75 °C
Note: Except for specially noted items, all applications are applicable to the Win-GRAF PAC (i.e., WP-8xx8, WP-5xx8-CE7, WP-8xx8-CE7, WP-9xx8-CE7, VP-x2x8-CE7, XP-8x38-CE6 PAC).
3. On Line Change: Replace the current running project to a new modified one without stopping the project.
8. Intelligent Win-GRAF 3G Solution:
- Only the WG-Communication Server (behavior like a Cloud Server) needs a public IP (support Domain Name). Other PACs and PCs that connect to this Server no need a public IP.
- The user can monitor the remote PAC by using a 3G wireless network or an intranet.
- The user can use the Win-GRAF Workbench to connect to a remote PAC to debug/update the Win-GRAF program or update the Win-GRAF PAC Driver.
- The PAC can actively send a Log File to a PC (WG-Communication-Server).
9. Support VS 2008 Development: The Win-GRAF PACs support to use VS 2008 (VB.net, C#) to develop user own HMI and data management programs, and can exchange variables with the Win-GRAF control programs.
10. Create Your Own Functions and Function Blocks: For some reason (like business protection, integration with your own product protocol, and etc.), you can develop your own functions and function blocks by VS 2008. Then, you can use these functions and function blocks in the Win-GRAF project.
Windows CE 7.0
.Net Compact Framework
FTP server, Web server (supports VB script, JAVA script), Embedded SQL server
English, German, French, Spanish, Russian, Italian, Japanese, Simplified Chinese, Traditional Chinese
IEC 61131-3 standard
LD, ST, FBD, SFC, IL. Support eLogger HMI : WP-8xx8, WP-5xx8-CE7, WP-8xx8-CE7, XP-8x38-CE6, WP-9xx8-CE7 and VP-x2x8-CE7 PAC.
Max. Code Size
3 ~ 15 ms for normal program
15 ~ 50 ms for complex or large program
Options: VS.NET 2008 (VB.NET, C#.NET, C)
Cortex-A8 (1.0 GHz)
microSD socket with one microSD card (support up to 32 GB)
RTC (Real Time Clock)
Provide second, minute, hour, date, day of week, month, year
64-bit Hardware Serial Number
Yes, for Software Copy Protection
Dual Watchdog Timers
Programmable LED Indicator
Yes (0 ~ 9)
Yes (8 bits)
VGA & Communication Ports
800 x 600, 1024 x 768
RJ-45 x 2, 10/100/1000M Base-TX
Internal communication with the high profile I-87K series modules in slots
RS-232 (RxD, TxD and GND); Non-isolation
RS-485 (Data+, Data-) with internal self-tuner ASIC; 3000 VDC isolated
RS-232/RS-485 (RxD, TxD, CTS, RTS and GND for RS-232; Data+ and Data- for RS-485); non-isolated
RS-232 (RxD, TxD, CTS, RTS, DSR, DTR, CD, RI and GND); non-isolated
I/O Expansion Slots
Note: For High Profile I-8K and I-87K Modules Only
Dimensions (W x L x H)
231 mm x 132 mm x 111 mm
DIN-Rail or Wall Mounting
-25 ~ +75 °C
-30 ~ +80 °C
Ambient Relative Humidity
10 ~ 90 % RH (non-condensing )
+10 ~ +30 VDC
Redundant Power Inputs
Yes, with one power relay (1 A @ 24 VDC) for alarm
1.1A, 5V supply to CPU and backplane, 4.9A, 5V supply to I/O expansion slots, total 30 W
9.1 W (0.38 A @ 24 VDC)
Protocols (Note that certain protocols require optional devices)
1 ~ 255, User-assigned by software
Modbus TCP/IP Master
Link to a max. of 100 devices that support the Standard Modbus TCP/IP Slave protocol
Modbus RTU/ASCII Master
A max. of 10 ports: COM1 ~ 14 (*). (To connect to other Modbus Slave devices) Support Multi-ports.
Modbus RTU Slave
A max. of 5 ports: COM1, one of COM2/3, COM4 ~ 8 (*). (For connecting ISaGRAF, PC/HMI/OPC Server and HMI panels.)
Modbus TCP/IP Slave
Two Ethernet ports (LAN1 & LAN2) support up to 32 connections. If the PAC uses 1 connection to connect each PC/HMI, it can connect to up to 16 PCs/HMIs; If the PAC uses 2 connections to connect each PC/HMI, it can connect to up to 32 PCs/HMIs; If one of the Ethernet port malfunctions, the other one can still be used to connect to the PC/HMI.
Web HMI Protocol
Ethernet Ports for connecting a PC running Internet Explorer.
Custom protocols can be applied at COM1~14 using Serial communication function blocks. (*)
I-7000 & I-87K RS-485 Remote I/O
One of COM2 ~ 3 supports I-7000 I/O modules, I-87K base + I-87K Serial I/O boards, or RU-87Pn + I-87K High Profile I/O boards as remote I/O. A max. of 255 I-7000/87K remote I/O modules can connect to one PAC.
M-7000 Series Modbus I/O
A max. of 10 RS-485 ports (COM1 ~ 14) (*) can support M-7000 I/O.
Each port can connect up to 32 M-7000 Modules.
Modbus TCP/IP I/O
LAN2 supports ICP DAS Ethernet I/O: I-8KE4-MTCP and I-8KE8-MTCP. If LAN2 malfunctions, it will automatically switch to LAN1 to continuously work. (The IP address for LAN1 and LAN2 should be set in the same IP domain).
Enable a max. of 8 pcs. I-8172W boards in slot 0~7 to be used to connect to FRnet I/O modules, such as FR-2053, FR-2057, FR-32R, FR-32P. Each I-8172W board can link to a max. of 256 DI plus 256 DO channels.
Provide functions to send email with a single attached file via the Ethernet port.
Used to exchange data between ICP DAS ISaGRAF Ethernet PACs via the Ethernet port. (LAN2 Port only)
SMS: Short Message Service
WP-84x7/88x7’s COM4/5 and WP-81x7’s COM1/COM5 can link to a GSM Modem to support SMS. The user can request data/control the controller via a cellular phone. The controller can also send data and alarms to the user’s cellular phone. (*) Optional GSM Modem: GTM-201-RS232 (850/900/1800/1900 GSM/GPRS External Modem)
COM4 or COM5 supports the ICP DAS MMICON. (*)
UDP Server & UDP Client : Exchange Message & Auto-report
LAN1 or LAN2 supports the UDP Server and UDP Client protocols allowing messages to be sent/received to/from a PC/HMI or other device. For example, data can be automatically reported to the InduSoft's RXTX driver.
TCP Client : Exchange Message & Auto-report
LAN1 or LAN2 supports the TCP Client protocol allowing messages to be sent/received to/from a PC/HMI or other device that supports the TCP server protocol. Ex: automatically report data to InduSoft's RXTX driver, or to connect a location camera.
Enable the I-8212W (2G/3G) card allowing short messages to be sent/received to/from or to access a dial up connection to link to the Internet and using a GPRS connection to send an email or communicate with remote stations using the "FTP Client" or the "TCP Client"/"UDP Server"/"UDP Client" protocols.
Support for the SQL Client function that allows data to be written (or read from) a Microsoft SQL Server (2000 SP3, 2005, 2008).
Hot-Swap and Redundant System
This redundant system has setup two "Active IP" address point to the active LAN1 and LAN2 ports always. One or more PC/HMI/SCADA can communicate with this redundant system via one of the two given active IP. So the PC/HMI/SCADA can access to the system easily without any notice about which WP-8xx7 is currently active.
Moreover, the new redundant system can integrate with the RU-87P4/87P8 Expansion Unit plus the I-87K high-profile I/O cards to support the hot-swap application. If the I/O card is damaged, the maintenance person just takes one good-card with same model number to hot-swap the damaged one without stopping this redundant system.
COM1, COM3 ~ COM14 (*) can connect to one I-7530 (converter: RS-232 to CAN) to support CAN/CANopen devices and sensors. One WP-8xx7 supports a max. of 10 RS-232 ports to connect a max. of 10 I-7530.
Enable the I-8123W CANopen Master card to connect to other CANopen Slave devices.
Enable I-87H17W modules in slots 0 to 7 used to communicate with other HART devices.
Enable the FTP Client to upload files from the PAC to a remote FTP server on a PC.
Provide support for the eLogger HMI. The user can design the HMI screen using the eLogger on the PC and then download it to the PAC to display the HMI on the PAC.
Optional I/O Functions (Refer to the ISaGRAF PAC I/O Selection Guide for I/O Module list)
High Speed PWM Module
I-7088, I-8088W, I-87088W: 8-ch. PWM outputs, software support 1 Hz ~ 100 KHz (non-continuous), duty: 0.1 ~ 99.9%
DO Module as PWM
8-ch. max. 250 Hz max. For Off=2 & On=2 ms .
Output square wave: Off: 2 ~ 32766 ms, On: 2 ~ 32766 ms.
Optional DO Boards: I-8037W, 8041W, 8041AW, 8042W, 8050W, 8054W, 8055W, 8056W, 8057W, 8060W, 8063W, 8064W, 8068W, 8069W. (Relay Output boards cannot generate fast square wave)
Counter, Encoder, Frequency
Parallel DI Counter
8-ch. max. For 1 controller. Counter val: 32-bit. 250 Hz max. Min. ON & OFF width must > 2 ms. Optional DI boards: I-8040W, 8040PW, 8042W, 8046W, 8048W, 8050W, 8051W, 8052W, 8053W, 8053PW, 8054W, 8055W, 8058W, 8063W.
Serial DI Counter
Counter input: 100 Hz max. Counter value: 0 ~ 65535 (16-bit)
Optional serial I-87K DI boards: I-87040W, 87046W, 87051W, 87052W, 87053W, 87053W-A5, 87054W, 87055W, 87058W, 87059W, 87063W.
Remote DI Counter
All remote I-7000 & I-87K DI modules support counters. 100 Hz max. value: 0 ~ 65535
High Speed Counter
I-87082W: 100 kHz max. 32 bit;
I-8084W : 250 kHz max. 32 bit
I-8093W: 3-axis Encoder Module, max. 1M Hz for quadrant input mode, max. 4M Hz for pulse/direction and cw/ccw input mode.
I-8084W: 250 kHz max., 4-ch encoder, can be pulse/direction, or Up/Down or A/B phase (Quad. mode); Not support Encoder Z-index.
I-87082W: 2-ch, 1 Hz ~ 100 kHz;
I-87088W: 8-ch, 0.1 Hz ~ 500 kHz;
I-8084W : 8-ch, 1 Hz ~ 250 kHz;
Can be integrated with one I-8091W (2-axis) or two I-8091W (4-axis)
* Note: The COM5 ~ COM14 ports are located in the expansion boards if they are installed in slots 0 ~ 7 of WP-8xx7.
* WP-8137/8147 has no COM3 & COM4.